The HR100R and HR100RS are ideal for single bedroom/bathroom applications such as hotel rooms, nursing homes and residential care homes. The HR100R features top access and is ideal for loft installations. The HR100RS features bottom access and is ideal for installation on the ceiling slab above a su...
The HR100R and HR100RS are ideal for single bedroom/bathroom applications such as hotel rooms, nursing homes and residential care homes. The HR100R features top access and is ideal for loft installations. The HR100RS features bottom access and is ideal for installation on the ceiling slab above a suspended ceiling.
The unit comes fitted with a single 2-speed motor, and provides continuous low volume ventilation with a boost option. A variety of control devices are available for manual or automatic speed control. An integral heat exchanger transfers heat from the outgoing stale air to the fresh air supply, raising the supply air temperature whilst at the same time reducing its relative humidity. Up to 77m³/h FID capacity (balanced airflow). As the unit provides superior control of condensation and odours best use would be in bathrooms or small internal rooms.
Installation The HR100R is compatible with 100mm diameter flexible ducting which fits onto the unit via the metal spigots and can be fastened using tape or worm drive clips. A 22mm diameter condensate drain connection is situated on the base of the unit, this should be connected to a suitable outlet for condensate drainage. The HR100R comes complete with a four core flying lead for connection to the chosen controller/power supply.
Volume m³/h (FID)
Controllers & Sensors
Trickle Boost Switch
Switch with Neon
Ambient Response Humidistat
7 Day Timeswitch
42 52 13
45 97 46
56 35 50
45 96 23
37 03 46
56 35 15
Typical Specification Supply and install a HR100R Wholehouse heat recovery unit as manufactured by:
Vent-Axia Clean Air Systems Fleming Way Crawley West Sussex RH10 9YX
Max ventilation rate
N° speed settings
Efficiency: The unit should retain up to 70% of the temperature differential of out going air.
Heat exchanger: should be of a multi plate cross-flow type constructed out of a polymeric plastic with ultra sonic welded joints.
Motor: should be a 2 speed 240V 50Hz A/C with sleeve bearings, greased for life. It shall operate up to an ambient temperature of 40°C and be fitted with a one shot thermal overload protective device.
Fan: The two polymeric fan wheels should be a centrifugal forward curve type on a common shaft.
Controls: The unit should be operated via a remote Trickle Boost switch or a humidistat. A light switch can be used providing a 'timed out' device is employed.
Ducting spigots: The unit should provide 100mm Ø x 50mm spigots for all duct connections. The unit cannot be handed. (Can be converted to flat ducting).
Filter: not fitted.
Condensation: the outlet provided should be 22mm Ø located on the underside of the unit.
Construction: the unit outer case is manufactured from white powder coated sheet metal.
dB(A) @ 3m
Mains electrical supply: 230VAC 50Hz.
Complies to the following approvals/directives: CE.