Round wall outlet ventilation grille for use with extraction or input ventilation systems, cooker hoods, tumble dryers, or hydroponics.
Flyscreen will help prevent insects from entering the property via your duct run.
Fits inside Kair 100mm Round Pipe (Part: "DUCVKC250") or 102mm flexible hose (part: "DUCP0092/102/35").
Easy to install 'clip-in' design. Built to last in the UK using high-quality Polystyrene/Polypropylene plastic Material.
Perfectly suited for ducting your Bathroom or Kitchen extractor fan, Hydroponics, In-Line Extract Fans, Tumble Dryer, or Cooker Hood.
This item can be used as a part of a long ductwork run for a variety of purposes including whole-house ventilation, passive stack vent, positive input ventilation, air conditioning, HVAC, and Heat Recovery systems.
Kair SYS-100 plastic rigid ducting is perfect for DIY and Trade use and provides superior airflow performance and durability versus flexible duct.
Suitable to use in compliance with Part F Building Regulations.
Genuine Kair Product & covered by the Kair 100% Satisfaction Guarantee. Compatible with the extensive Kair SYS-100 range of fittings, outlets, and grilles.
|Round System (mm)||100|
|Product Type||Wall Vent|
|Product Group||Plastic Ducting|
|Spigot size (mm)||34 x 96 x 96|
|Packaged Weight (Kg)||0.044|
|Packaged Length (mm)||128|
|Packaged Width (mm)||38|
|Packaged Height (mm)||128|
|Temp Max (°C)||60|
|Temp Min (°C)||-15|
|Polypipe / Domus (similar)||4804|
|Pressure Loss (Pa) 15 l/s||22.5|
|Pressure Loss (Pa) 30 l/s||75.8|
|Pressure Loss (Pa) 60 l/s||291.9|
Your question will be sent to a member of our team. We'll email you the answer and post it on this page. If your question is about an order you already placed, please use our Contact Form to reach the customer service team.
I'm fitting an extraction system for my bathroom based on the Manrose inline fan. I am using 100 mm round pipework but need to switch to the rectangular 110 flat channel to follow the roofline down across the plate to the back of the soffit board where i hope to convert back to 100mm round to exit the underside of the soffit through the Kair 100 mm round grille with fly screen. the pitch of my roof is considerably less than 45 degrees so fixed 45 bends at either end of the flat channel will not get me at the correct angle to connect. can you get flexible bends to give me the angles i need or is the only solution to use short pieces of flexible ducting to connect ?
I note that the inside push-fits into a 100mm duct, but what is the diameter of the outside? Has it 2 screwholes for fixing to the external wall?
|Customers who bought this product also purchased|
|Ducting System||Actual dimensions (mm)||Space requirements (mm)||Airflow mm²|
For 4" (100mm) extractor fans or for low power cooker hoods up to 250m³/hour
|System 100 - Round||100||106||7,854|
|System 100 - Rectangular||110 x 54||116 x 60||5,940|
For medium extraction rates or if available depth is limited up to 500m³/hour
|System 125 - Round||125||131||12,272|
|System 125 - Rectangular||150 x 70||156 x 76||10,500|
For 6" (150mm) extractor fans or for high power cooker hoods up to 500m³/hour & above
|Megaduct 220 - Rectangular||220 x 90||227 x 97||17,968|
|System 204 - Rectangular||204 x 60||210 x 66||12,240|
|System 150 - Round||150||156||17,671|
|System 150 - Rectangular||180 x 90||186 x 96||16,200|
For a shallow space, such as ceiling voids or under floor, where high extraction rates are not needed:
|System 300 - Rectangular||308 x 29||314 x 35||8,932|
|System 225 - Rectangular||234 x 29||240 x 35||6,786|
| System 100 |
| System 125|
| System 150|
|System 204||System 225|
|System 220||System 300|
|Actual Dimensions (mm) Space Requirements (mm)|