Mixed Flow Inline Duct Fan for 100mm ducting.
In Line Mixed Flow fans offer two and half times the pressure of conventional axial fans, are dimensionally more compact making them ideal for many ducted applications. The impeller blade design with guide vanes provides optimum pressure characteristics and simple connectivity and quieter more efficient running provides the complete solution.
The ACM Mixed Flow In-Line fan can operate in both horizontal and vertical positions and can be mounted to meet its optimum performance.
All motors are fitted with Standard Thermal Overload Protection. (S.T.O.P.). Designed for ambient temperatures up to +50°C.
Size 100 and 125 with shaded pole motors. Size 150, 200, 250 and 315 with capacitor start and run motors. All sizes are Class II appliances except ACM250 and ACM315 which is Class I Supply voltage 220-240V/1/50Hz.
Supply and install the ACM range of commercial In-line fans as manufactured by Vent-Axia Ltd, Fleming Way, Crawley, West Sussex, RH10 9YX, Telephone: 01293 526062.
The fan should be of the mixed flow design specifically for use with rigid and flexible ducting with energy efficiency and low sound levels in mind. The fan shall be fitted within the ducted system and isolated from the building structure by means of Anti- Vibration mountings.
The fans should be dimensionally compact saving weight and installation costs. The casing should be manufactured from galvanised sheet steel and manufacture is controlled to BS EN ISO 9001.
The fan should be fully speed controllable by using a variable speed controller.
The fan should be controlled by humidity, air quality or PIR sensor.
The fan motor should be removable by means of 2 Clip Bands for ease of maintenance.
Motors should have ball bearings greased for life to allow the fan to be installed at any angle and should have Class B insulation to allow the fan to work satisfactorily in ambient air temperatures from -5°C to +50°C and should be fitted with Standard Thermal Overload Protection (S.T.O.P.).
|Product Category||In-Line Fans|
|Round System (mm)||100|
|Product Type||Mixed Flow In-Line Fan|
|Product Group||Ventilation Fan|
|Spigot size (mm)||97|
|Power Min (Watts)||18|
|Power Max (Watts)||23|
|Decibel Rating (dB) - Low||20|
|Decibel Rating (dB) - Max||23|
|Packaged Weight (Kg)||2.061|
|Packaged Length (mm)||230|
|Packaged Width (mm)||210|
|Packaged Height (mm)||360|
|Economy Delivery||Not Eligible|
|Manufacturer Product Code||17104010|
|Vent Axia (similar)||ACM100|
|Airflow Performance (l/s) - Low||70|
|Airflow Performance (l/s) - High||80|
|Airflow Performance (m³/h) - Low||252|
|Airflow Performance (m³/h) - High||288|
Your question will be sent to a member of our team. We'll email you the answer and post it on this page. If your question is about an order you already placed, please use our Contact Form to reach the customer service team.
Can the fan be fixed into the bathroom wall so that the steam is taken outside?
Do you also supply ventaxia ACM100T 17104020 and if so how much is it? can this be put into the bathroom wall so that the steam is taken outside?
Is there a maximum duct length for the extractor? I'm looking to run a 6m rigid duct length in total vertically. How much will it affect the performance?
Thank you for your question. The ACM fan does a 8mtr straight duct run and a 6mtr duct run with two bends. The ACM Mixed Flow In-Line fan can operate in both horizontal and vertical positions and can be mounted to meet its optimum performance.
is this humidistat controlled or timer or both
This unit is a 'standard' in-line fan without over-run timer which is designed to be switched, or used with an optional controller.
If you are looking for an optional humidistat you could use the Kair Humidistat Controller.
We have an internal lavatory and due to the lack of external wall access we will have to vent the extractor unit into the waste or soil pipe. Is this fan suitable and is there a non return valve arrangement that would prevent the back fill of odour from the waste or soil pipe? many thanks
Thank you for your question. If your duct run is 8mtrs straight or 6mtr with two bends then this fan will do you application. The backdraught shutter is product code QS256 you may also require product code DOM120.
Circular adapter for System 100 ducting to 110mm Soil Pipe
System 100 End (Male - connects into System 100 straight ducting DUCVKC250):
Outer Diameter: 98mm
Inner Diameter: 95mm
System 110 End (Usually Female dependant on manufacturer - connects over 110mm OD straight pipe):
Outer Diameter: 113mm
Inner Diameter: 110mm
If you require any further assistance please do not hesitate to contact me on 0208 463 9683
Hi I am currently in the middle of a loft conversion and the layout will be open plan where the bedroom and shower area to the back is without a door. I plan on having a walk in shower that is enclosed from floor the ceiling. In this scenario would the fan be better of inside this area or outside? Thanks
Thank you for your question. The in-line fan can be situated inside or outside the area and ducted to the extract valve. Could you advise me how long your duct run is from the area to the outside wall.
Hi What thermostat would you recommend to operate this product Thanks
Can this be wired to an extractor fan so that when the extractor fan is switched on the inline comes on at the same time I want to assist the extractor fan in removing steam etc, so my intention is to put this in the middle of the ducting run as the extractor is not strong enough by itself
Hi I know this might seem a stupid question, dose it connect to the lighting circuit or a ring main
Thank you for your question. The wiring diagram can be found on the PDF for this fan on our web site. I will send this to you on a separate e-mail.
do you supply the vent axia ACM17104010D
Hi, can this be used as a constant trickle extract fan, and boost with a light? thank you
Dear Sir or Madam, I would like to use this fan to extract warm air from my loft on hot days. It would be 'in line' with about 2m of ducting each side with two bends max. Could you please tell me whether the unit is compatible with a thermostat, and if so whether you stock the appropriate one? Regards and thanks
Hi, can this be wired to a simple on/off switch?
|Customers who bought this product also purchased|